CITY OF ALAMO
2020 ANNUAL DRINKING
WATER QUALITY REPORT
(CONSUMER CONFIDENCE REPORT)
(956) 787-2232 (956) 787-8321 (956) 787-0006
SPECIAL NOTICE: Some people may be more vulnerable to contaminants in drinking water than the general population. Immuno-compromised persons such as persons with cancer undergoing chemotherapy, persons who have undergone organ transplants, people with HIV/AIDS or other immune system disorders, some elderly and infants can be particularly at risk from infections. These people should seek advice about drinking water from their health care providers. EPA/Centers for Disease Control and Prevention (CDC) guidelines on appropriate means to lessen the risk of infection by Cryptosporidium and other microbial contaminants are available from the Safe Drinking Water Hotline 1-800-426-4791.
PUBLIC PARTICIPATION: Regular Commissioner’s meetings are held the 1st and 3rd Tuesdays of the month, at 6:00 pm, in the Municipal Building located at 420 N Tower Road, Alamo, Texas.
ALL DRINKING WATER MAY CONTAIN CONTAMINANTS. When drinking water meets federal standards, there may not be a health-based benefit to purchasing bottled water or point of use devices. Drinking water, including bottled water, might reasonably be expected to contain at least small amounts of some contaminants. The presence of contaminants does not necessarily indicate that water poses a health risk. Information about contaminants and potential health effects can be obtained by calling the EPA’s safe drinking water hotline at 1-800-426-4791.
The TCEQ completed an assessment of our water and results indicate that our sources have a low susceptibility to contaminants. The sampling requirements for our water system are based on this susceptibility and previous sample data. Any detections of these contaminants may be found in this Consumer Confident Report. In order to ensure that tap water is safe to drink, EPA prescribes regulations which limit the amount of certain contaminants in water provided by public water systems. FDA regulations establish limits for contaminants in bottled water which must provide the same protection for public health. For more information on source water assessments and protection efforts at our system contact Bobby Salinas at (956)787-0006.
Este informe incluye informacion importante sobre el agua potable. Si tiene preguntas o comentarios sobre este informe en espanol, favor de llamar al tel. (956) 787-2232 para hablar con una persona bilingue en espanol.
NOTICE MAILED 06/30/2021
WATER SOURCES: Our raw water supply is derived from the Rio Grande River and is delivered to us via numerous miles of river, dams, cement canals and cement piping which is owned and operated by the Hidalgo County Irrigation District No 2. As water is delivered, it dissolves naturally occurring minerals and even picks up substances resulting from the presence of animals or from human activity. TCEQ will be reviewing all of Texas drinking water sources. The source water assessment has been completed and the report, which will be available this year, will allow us to focus on our source water protection activities. Contaminants that might be expected in untreated water include: microbial contaminants such as viruses and bacteria; inorganic contaminants such as salts and metals; pesticides and herbicides, organic chemicals from industrial or petroleum use and radioactive contaminants resulting from oil and gas production and mining activities.
ABOUT THE ENCLOSED PAGES: the enclosed pages list all of the federally regulated or monitored constituents, which have been found in your drinking water, US EPA requires water systems to test up to 97 constituents.
SECONDARY CONSTITUENTS: Many constituents such as calcium, sodium, or iron, which are often found in drinking water, can cause taste, color, and odor problems. The taste and odor constituents are called secondary constituents and are regulated by the State of Texas not EPA. These constituents are not cause for health concerns. Therefore, secondary’s are not required to be reported in this document but they may greatly affect the appearance and taste of your water.
MAXIMUM CONTAMINANT LEVEL (MCL)-The highest permissible level of a contaminant in drinking water. MCLs are set as close to the MCLGs as feasible using the best available treatment technology.
MAXIMUM CONTAMINANT LEVEL GOAL (MCLG)-The level of a contaminant in drinking water below which there is no known or expected health risk, MCLGs allow for a margin of safety.
MAXIMUM RESIDUAL DISINFECTANT LEVEL (MRDL)-The highest level of disinfectant allowed in drinking water. There is convincing evidence that addition of a disinfectant is necessary for control of microbial contaminants.
MAXIMUM RESIDUAL DISINFECTANT LEVEL GOAL (MRDLG)-The level of a drinking water disinfectant below which there is no known or expected risk to health. MRDLGs do not reflect the benefits of the use of disinfectants to control microbial contamination.
TREATMENT TECHNIQUE (TT)-A required process intended to reduce the level of a contaminant in drinking water.
ACTION LEVEL (AL)-The concentration of a contaminant which, if exceeded, triggers treatment or other requirements that a water system must follow.
NTU – Nephelometric Turbitity Units (a measure of turbidity) na – not applicable
pCi/l – picocuries per liter (a measure of radioactivity)
ppb – parts per billion or micrograms per liter (mg/l)
ppq – parts per quadrillion or pictograms per liter(pg/L)
MFL – million fibers per liter (a measure of asbestos)
ppm – parts per million or milligrams per liter (mg/l)
ppt – parts per trillion or nanograms per liter
Recommended Additional Health Information for Lead
“If present, elevated levels of lead can cause serious health problems, especially for pregnant women and young children. Lead in drinking water is primarily from materials and components associated with service lines and home plumbing. This water supply is responsible for providing high quality drinking water, but cannot control the variety of materials used in plumbing components. When your water has been sitting for several hours, you can minimize the potential lead exposure by flushing your tap for 20 seconds to 2 minutes before using water for drinking or cooking. If you are concerned about lead in your water, you may wish to have your water tested. Information on lead in drinking water, testing methods and steps you can take to minimize exposure is available from the safe Drinking Water Hotline at www.epa.gov/safewater/lead.
LEAD AND COPPER
|YEAR||CONTAMINANT||THE 90TH PERCENTILE||NUMBER OF SITES EXCEEDING ACTION LEVEL||ACTION LEVEL||UNIT OF MEASURE||SOURCE OF CONTAMINANT|
|2019||Lead||3.5||0||15||ppb||Corrosion of household plumbing systems; erosion of natural deposits.|
|2019||Copper||0.068||0||1.3||ppm||Corrosion of household plumbing systems; erosion of natural deposits;leaching from wood preservatives.|
|YEAR||CONTAMINANT||AVERAGE LEVEL||MINIMUM LEVEL||MAXIMUM LEVEL||MCL||MCLG||UNITOF MEASURE||SOURCE OF CONTAMINANT|
|2020||Fluroide||0.64||0.64||0.64||4||4||ppm||Erosion of natural deposits; water additive which promotes strong teeth; discharge from fertilizer and aluminum factories.|
|2020||Nitrate||.20||.20||.20||10||10||ppm||Runoff from fertilizer use; leaching from septic tanks, sewage;erosion of natural deposits.|
|2020||Gross beta emitters||6.0||6.0||6.0||50||0||pCi/L||Decay of natural and man-made deposits.|
|2020||Gross alpha||4||4||4||15||0||pCi/L||Erosion of natural deposits.|
ORGANIC CONTAMINANTS-Testing waived, not reported or none detected.
MAXIMUM RESIDUAL DISINFECTANT LEVEL-System must complete and submit disinfection data on the Surface Water Monthly Operations Report. On the CCR report, the system must provide disinfectant type, minimum, maximum and average levels.
|YEAR||DISINFECTANT||AVERAGE LEVEL||MINIMUM LEVEL||MAXIMUM LEVEL||MRDL||MRDLG||UNIT OF MEASURE||SOURCE OF CHEMICAL|
|2020||Chlorine Dioxide||.4||.4||.8||.80||.80||ppm||Disinfectant used to control microbes.|
|YEAR||CONTAMINANT||AVERAGE LEVEL||MINIMUM LEVEL||MAXIMUM LEVEL||MCL||MCLG||UNIT OF MEASURE||SOURCE OF CONTAMINANT|
|2020||Total haloacetic acids||6||6.7||12||60||–||ppb||Byproduct of drinking water disinfection.|
|2020||Total Trihalomethanes||12.3||2.5||22||80||–||pbb||Byproduct of drinking water disinfection.|
|2020||Chlorite||.390||0.104||0.457||1||.08||pbb||Byproduct of drinking water disinfection.|
Unregulated Initial Distribution System Evaluation for Disinfection Byproducts – Waived or not yet sampled.
Bromoform, chloroform, dislorobromomethane and dibromochloremethane are disinfection byproducts. There is no maximum contaminant level for these chemicals at the entry point to distribution.
|YEAR||CONTAMINANT||AVERAGE LEVEL||MINIMUM LEVEL||MAXIMUM LEVEL||UNIT OF MEASURE||SOURCE OF CONTAMINANT|
|2020||Chloroform||1.29||1.0||5.8||ppb||Byproduct of drinking water disinfection.|
|2020||Bromofrom||8.33||1.3||58.2||ppb||Byproduct of drinking water disinfection.|
|2020||Bromodichloromethane||1.9||1.0||8.4||ppb||Byproduct of drinking water disinfection.|
|2020||Dibromochloromethane||4.4||1.2||6.2||ppb||Byproduct of drinking water disinfection.|
TURBIDITY is a measurement of the cloudiness of the water caused by suspended particles and has no health effects. However, turbidity can interfere with disinfection and provide a medium
for microbial growth. Turbidity may indicate the presence of disease causing organisms. These Organisms include bacteria, viruses and parasites that can cause symptoms such as nausea, cramps,
diarrhea and associated headaches. We monitor it because it is a good indicator of water quality and the effectiveness of our filtration system and disinfectants.
|YEAR||CONTAMINANT||HIGHEST SINGLE MEASUREMENT||LOWEST MONTHLY % OF SAMPLES MEETING LIMITS||TURBIDITY LIMITS||UNIT OF MEASURE||SOURCE OF CONSTITUENT|
TOTAL ORGANIC CARBON (TOC) has no health effects. The disinfectant can combine with TOC to form disinfection byproducts. Disinfection is necessary to ensure that water does not have unacceptable levels of pathogens. Byproducts of disinfection include trihalomethanes (THMs) and haloacetic acids (HAA) which are reported elsewhere in this report. The percentage of Total Organic Carbon (TOC) removal was measured each month and the system met all TOC removal requirements set, unless a TOC violation is noted in the violations sections.
|YEAR||CONTAMINANT||AVERAGE LEVEL||MINIMUM LEVEL||MAXIMUM LEVEL||UNIT OF MEASURE||SOURCE OF CONTAMINANT|
|2020||Source water||3.8||3.5||4.3||ppm||Naturally present in the environment.|
|2020||Drinking water||2.4||1.80||2.9||ppm||Naturally present in the environment.|
|2020||Removal ratio||27.3||18.0%||34.5%||% removal*||N/A|
*removal ratio is the percent of YOC removed by the treatment process divided by the percent of TOC required by TCEQ to be removed.
TOTAL COLIFORM bacteria are used as indicators of microbial contamination of drinking water because testing for them is easy. While not disease causing organisms themselves, they are often found in association with other microbes that are capable of causing disease. Coliform bacteria are more hardy than many disease causing organisms; therefore, their absence from water is a good indication that the water is microbiologically safe for human consumption.
|YEAR||CONTANIMANT||HIGHEST MONTHLY NUMBER OF POSITIVE SAMPLES||MCL||UNIT OF MEASURE||SOURCE OF CONTAMINANT|
|2020||Total Coliform||0||*||Naturally present in the environment.|
*Two or more coliform found samples in any single month.
Secondary and Other Constituents Not Regulated – (No associated adverse health effects)
|YEAR||CONSITUTENT||AVERAGE LEVEL||MINIMUM LEVEL||MAXIMUM LEVEL||SECONDARY LIMIT||UNIT OF MEASURE||SOURCE OF CONSTITUENT|
|2020||Bicarbonate||163||163||163||NA||ppm||Corrosion of carbonate rocks such as limestone.|
|2020||Chloride||241||241||241||300||ppm||Abundant naturally occurring element; used in water purification; byproduct of oil filed activity.|
|2019||Hardness as Ca/Mg||312||312||312||NA||ppm||Naturally occurring calcium and magnesium|
|2020||pH||7.8||7.8||7.8||>7.0||units||Measure of corrosivity of water.|
|2019||Sodium||217||217||217||NA||ppm||Erosion of natural deposits; byproduct of oil field activity.|
|2020||Sulfate||330||330||330||300||ppm||Naturally occurring; common industrial byproduct; byproduct of oil field activity.|
|2020||Total Alkalinity As CaCO3||127||116||132||NA||ppm||Naturally occurring soluble mineral salts|
|2020||Total Dissolved Solids||1020||1020||1020||1000||ppm||Total dissolved mineral constituents in water.|
|YEAR||CONTAMINANT||HIGHEST LEVEL DETECTED||RANGES OF LEVEL DETECTED||MCLG||MCL||UNIT OF MEASURE||SOURCE OF CONTAMINENT|
|2020||ARSENIC||0.0020||0.0020||0||10||ppb||Erosion of natural deposits;Runoff from orchards;Runoff from glass and electronics production wastes.|
|2020||Barium||0.0783||0.0783-0.0783||2||2||ppm||Discharge of drilling wastes;Discharge from metal refineries;Erosion of natural deposits|
|2020||Nitrate(measured as Nitrogen)||.20||.20-.20||10||10||ppm||Runoff from fertilizer use;Leaching from septic tanks,sewage;Erosion of natural deposits|
|2020||Nitrite(measured As Nitrogen)||.01||.01-.01||1||1||ppm||Runoff from fertilizer use;Leaching from septic tanks,sewage;Erosion of natural deposits|
|2020||Selenium||.0036||.0036-.0036||50||50||ppb||Discharge from petroleum and metal refineries;Erosion of natural deposits; Discharge from mines.|
|2020||Cyanide||60||60-60||200||200||ppb||Discharge from petroleum and metal refineries;Erosion of natural deposits; Discharge from mines.|
|COLLECTION DATE||CONTAMINANT DETECTED||HIGHLEST LEVEL DETECTED||RANGE OF LEVELS||MCLG||MCL||UNIT OF MEASURE||SOURCE OF CONTAMINENT|
|02/21/2014||Combined Radium 226/228||0.91||0.91– 0.91||0||5||pCi/L||Erosion of natural deposits.|
*EPA considers 50 pCi/L to be the level of concern for beta particles
|Beta/photon emitters||6.0||6.0-6.0||0||50||pCi/L*||Decay of natural and man-made deposits|
|2020||Uranium||4.7||4.7-4.7||0||30||ug/l||Erosion of natural deposits.|
Lead and Copper Rule
The Lead and Copper Rule protects public health by minimizing lead and copper levels in drinking water, primarily by reducing water corrosivity. Lead and copper enter drinking water mainly from corrosion of lead and copper containing plumbing materials.
Violation Type Violation Begin Violation End Violation Explanation
IN THE WATER LOSS AUDIT SUBMITTED TO TEXAS WATER DEVELOPMENT BOARD FOR THE TIME PERIOD OF JANUARY 2020 OUR SYSTEM LOST AN ESTIMATED TOTAL OF
32 GALLONS PER CAPITA PER DAY (GPCD) OF WATER.
A SOURCE WATER ASSESSMENT FOR YOUR DRINKING WATER SOURCE(S) IS CURRENTLY BEING CONDUCTED BY THE TCEQ AND SHOULD BE PROVIDED TO US THIS YEAR. THE REPORT WILL DESCRIBE THE SUSCEPTIBILITY AND TYPES OF CONSTITUENTS THAT MAY COME INTO CONTACT WITH YOUR DRINKING WATER SOURCE BASED ON HUMAN ACTIVITIES AND NATURAL CONDITIONS. THE INFORMATION IN THIS ASSESSMENT WILL ALLOW US TO FOCUS ON OUR SOURCE WATER PROTECTION STRATEGIES.